Honeywell S8610U3009 Universal Intermittent Pilot Ignition Module replaces multiple field installed intermittent pilot modules supplied by Honeywell, Robertshaw, Johnson Controls and UTEC (HSC). Uses existing intermittent pilot burner. Includes cross reference, instructions and accessories for easy replacement.
- Replaces over 400 White-Rogers, Robertshaw and Honeywell intermittent pilot ignition modules
- Provides ignition sequencing, flame monitoring and safety shutoff for intermittent pilot warm air furnaces and heating appliances
- Provides 100 percent pilot gas shutoff if pilot fails to light; after 5-minute delay, trial for ignition is repeated. Ignition trial/delay sequence is repeated until the appliance lights or call for heat is removed
- For use with Natural or LP gas
- For use in single rod or dual rod / remote sense applications
- Includes spark cable adapters to allow field replacement of both Honeywell and competitive controls without replacing existing spark cable.
- TH-W should be connected to 24VAC from the thermostat
- 24V GND should be connected to the un-switched leg of 24VAC transformer
- 24V should NOT be connected if P1 vent damper is not used
Replaces the following Honeywell models
S86A1001, S86A1019, S86A1027, S86A1035, S86B1009, S86B1017, S86B1025, S86C1007, S86C1015, S86C1023, S86C1031, S86C1049, S86C1056, S86D1005, S86D1013, S86D1021, S86E1002, S86E1010, S86E1028, S86E1036, S86E1044, S86E1051, S86E1069, S86E1077, S86E1101, S86E1119, S86E1127, S86F1000, S86F1018, S86F1026, S86F1042, S86F1059, S86F1067, S86F1075, S86F1083, S86F1091, S86G1008, S86G1016, S86G1024, S86G1032, S86G1057, S86G1073, S86H1006, S86H1014, S86H1022, S86H1048, S86H1055, S86H1063, S86H1089, S86H1097, S86H1105, S86H1113, S86H1121, S86H1139, S86H1147, S90A1005, S90B1003, S90B1011, S860C1000, S860D1009, S860D1017, S8600A1001, S8600B1009, S8600B1025, S8600B3005, S8600B3013, S8600C1015, S8600C3003, S8600F1000, S8600F1034, S8600F1042, S8600H1006, S8600H1014, S8600H1022, S8600H1048, S8600H1055, S8600H1063, S8600H1071, S8600H1089, S8600H1097, S8600H1105, S8600H3002, S8600H3010, S8600M1005, S8600M1013, S8600M1021, S8600M2003, S8600M3001, S8600M4009, S8610A1009, S8610B1007, S8610B1015, S8610B1023, S8610B3003, S8610C1005, S8610C1013, S8610C3001, S8610F1008, S8610F1016, S8610F1024, S8610F1032, S8610H1004, S8610H1012, S8610H1020, S8610H1038, S8610H1046, S8610H1053, S8610H1061, S8610H1079, S8610H1095, S8610H3000, S8610H3018, S8610H3026, S8610M1003, S8610M1011, S8610M1029, S8610M3009, S8610M3017, S8610U1003, S8610U1011, S8620C1003, S8620C1011, S8620H1002, S8620H1010, S8620H1028, S8660D1002, S8660D1010, S8660J1008, S8660J1016, S8660J1024, S8660K1006, S8660K1014, S8660K1022, S8670D1000, S8670D1018, S8670D1026, S8670D3006, S8670D3014, S8670E1007, S8670E3003, S8670J3002, S8670J3010, S8670K3000, S8680J1004
INSTALLATION TIPS - LED Error Codes
For quick installation tips Click Here
|OFF: No call for heat, TH-W does not have 24VAC present|
|Fast Flash: Power up - internal check|
|Heart beat (1/2 sec bright, 1/2 dim cycles)
Normal start up, ignition sequence started
|4 secs on then x flashes: Device in run mode. "x" = flame current to the nearest microamp|
|2 flashes: 5 minute retry delay|
|3 flashes: Flame failed during run|
|4 flashes: Flame sensed out of sequence4 flashes: Flame sensed out of sequence|
|5 flashes: Damper error. Make sure 24V terminal is not connected if P1 plug is not used|
|6 flashes: Control internal error|
|7 flashes: Flame rod shorted to ground|
|8 flashes: Low secondary voltage supply. Check transformer and AC line|
Check the ratings given in the instructions to make sure the S8610U module is suitable for your application. Needs to be installed by experienced licensed professional. Failure to follow instructions carefully can result in injury or cause damage to the product. Explosion hazard with risk of serious injury or death if installed improperly. After installation is complete, check out operation as provided in the instructions.
DISCLAIMER: Acr4sale is not responsible for how the product is installed.